We recently received the following question from a lot owner about time to comply with a defect notice for a fire door replacement due. Peter Berney, Solutions in Engineering has provided the following response.
Question: My apartment was listed as “critical” for a fire door replacement. Strata will cover the costs, but I am wondering how long the body corporate has to comply with the order.
My building recently had all our entrance fire doors inspected and it was determined that my apartment entrance fire door was not actually a fire door.
It was listed as “critical” for a fire door replacement. Strata will cover the costs, but I am wondering how long the body corporate has to comply with the order for the fire door replacement.
At present, the earliest they can fix the issue is a few week’s time. I am concerned as I’m not sure where we stand with regards to insurance etc until the work has been carried out.
Answer: If it’s critical they have 30 days if it’s not critical then before the next inspection.
Time limit to repair would depend on a couple of things, for example, is it because of a fire contractors defect notice? If it’s critical they have 30 days, if it’s not critical then before the next inspection.
Qld Fire doors for residential under MP6.1 is every 12 months.
This situation would fall into the 30 days category mentioned above. As there needs to be a work order to replace the door, I doubt insurance would be affected if something were to occur before the door is replaced. This would be because the Body corporate committee is carrying out the work as fast as reasonably practicable.
This post appears in Strata News #186.
- QLD: Q&A Fire doors kept open – is committee neglecting responsibilities about fire safety?
- QLD: Q&A Fire doors failed inspection due to unauthorised security doors
- QLD: Fire alarms and False Fire Alarms – Who makes sure we all get out?
This article is not intended to be personal advice and you should not rely on it as a substitute for any form of advice.